Biogas generator set maintenance method
biogas generator set should be used according to the specific operating conditions necessary to maintain, using the specified fuel, smooth and timely change oil and coolant, insist on biogas generator set clean, regular check leakage and loose status, to ensure that the normal strong work, prolong service life.
1, filter maintenance:
1) air filter: every 50 hours, with air compressor mouth blowing a liquidation. Every work 500 hours or when the alarm installation red to change, change after filter press the top button will indicate attention;
2. Oil filter: after the period must be changed, changed once every 500 hours or six months later. Change filter is running for 10 minutes, if changing the oil filter must smooth oil change at the same time;
(3) diesel filter: after the period must be changed, changed once every 500 hours or six months later. Change filter and then start running for 10 minutes;
(4) coolant filter: use 200 hours or three months must change. After every 500 hours or change once a year.
2, smooth oil change: after the period must be changed, after every 500 hours or change once every six months. Change the oil when different brands, different models of oil shall not be mixed use. Smooth oil change necessary to change the oil filter.
3, coolant change: use 200 hours or three months must change. After every 500 hours or change once a year. Pay attention to just stop unit, 15 minutes must not open the tank cover. Avoid water vapor jet cuts.
4, daily routine or check items: before starting the check and remove the oil, water and air leakage phenomenon, wipe the genset appearance, insist on diesel engine and the environment clean and tidy appearance; Adhere to the cleanness of the whole machine unit. Avoid accumulated water, iron and sundry; Check the fuel tank oil level. Ensure emergency power supply unit; Check machine oil surface height, can have higher abnormal or landing, and find out the reasons, the lack of timely add; Check the water tank water level; Check the battery voltage, pay attention to add distilled water; Check the maintenance cover loose condition and various cohesive components screw, nut fastening; Enter the should pay attention to heat preservation in winter, and injecting antifreeze enough in the tank.
5, biogas power generation unit running test: the fuel tank should be thoroughly clean every week, to avoid the accumulated water, iron and impurities, the unit needs to start a weekly test run operation, examine the dashboard lights, no-load running 5 minutes, take a moderate amount of load running 15 - every half month 30 minutes; Firmness of tank belt check once a week, wear, if any, should be changed.
Looking for a producer to fix your best standby generator problems? Then contact the best standby generator experts at XINSHENGAN Power Technology (Shandong) Co., Ltd., offering a wide range of products across the global market. Visit Xinshengan Generators Sets to find our best offer!
Get cost effective and professional gas generator manufacturers advice for your solution at Xinshengan Generators Sets. XINSHENGAN Power Technology (Shandong) Co., Ltd. expert is your first choice!
XINSHENGAN Power Technology (Shandong) Co., Ltd. who primarily serve our consumers need to consider offering their products in an industrial generator manufacturers such as best standby generator to take advantage of the growing interest from consumers in supporting cheapest natural gas generator.
An easy and inexpensive best standby generator solution can be easily obtained now through purchasing a best standby generator standby generator manufacturers online. Find your solution at Xinshengan Generators Sets, your demand will be satified.