The technology of gas generator set maintenance
Level of technical maintenance cumulative gas generator running 100 h or every other month, should carry on the level of technical maintenance. Complete daily maintenance of all project. For battery maintenance, add supplementary fluid, charging. Check the triangle rubber belt tensioning degree. Disassemble the body under observation window cover plate, pull open the coarse mesh spring lock, remove the filter in the diesel fuel for cleaning, then blowing off. Clean air filter and breathing air filter. Every Zooh clean oil filter, centrifugal filter. Replace the oil sump of engine oil to the generator set each nozzle with grease or oil. Clean water radiator inspect generator within the wiring is reliable. Make a record level of maintenance. Secondary technical maintenance of biomass gas generator run 500 h or every six months, should be the secondary technical maintenance. To complete the project stipulated in the level of technical maintenance. Check the spark plug, clean up the carbon deposition, and adjust the clearance between 0. 6mm。 As between the check valve and ignition timing, if necessary, adjust. Check the sealing condition of inlet and exhaust valves. Check the sealing condition of cylinder liner seal hydrosphere. Check for leaks oil cooler and cooling water radiator, oil spill. For connecting rod nut screw, crankshaft, cylinder head nuts etc. Check the electrical equipment for burning phenomenon, the wire connection is firm. Cleaning oil pipe line, including cleaning the oil pan, oil pipe, oil cooler, etc. Clean the cooling system channel. Clean up the dust unit control panel. Make a record level 2 maintenance. Level 3 technical maintenance of biomass gas generator run 1000 a 1500 h or every other year, should be level 3 technical maintenance. Complete secondary technical maintenance of project. Check the wear condition of cylinder head components. Check piston connecting rod component in the abrasion of the components. Check the components of the crankshaft. Check the drive mechanism and distribution phase. Check the oil pump, fresh water pump. Check the starter motor. Check the cover and security devices research alarm system inspection engine connected to the generator do level 3 maintenance record new shengan power of science and technology ( Shandong) Co. , LTD. , is a long-term committed to the development of new environmental protection power equipment, production, sales and after-sale is a body comprehensive high-tech enterprises.