In the cold winter, the engine is difficult to start. If you add cold water before starting, it is easy to freeze during the water filling process or when the water is not started in time. The water tank and the water inlet pipe are likely to freeze, causing the water to be unable to circulate, or even Crack the water tank. Filling with hot water, on the one hand, can increase the temperature of the engine for easy starting; on the other hand, it can try to avoid the above freezing phenomenonAntifreeze should be high qualityAt present, the quality of antifreeze on the market is uneven, and many are shoddy. If the antifreeze does not contain preservatives, it will severely corrode engine cylinder heads, water jackets, radiators, water blocking rings, rubber parts and other components. At the same time, a large amount of scale will be generated, which will cause poor engine heat dissipation and cause engine overheating failure. Therefore, products from regular manufacturers must be used.Replenish soft water in timeAfter filling the water tank with antifreeze, if the liquid level of the water tank is found to be lowered, under the premise of ensuring no leakage, only need to fill with clean soft water (distilled water is better), because the generally used glycol type antifreeze has a high boiling point , What evaporates is the water in the antifreeze, no need to replenish the antifreeze, just add soft water. It is worth mentioning that: Never add hard water that has not been softened.Drain antifreeze in time to reduce corrosionWhether it is ordinary antifreeze or long-lasting antifreeze, it should be released in time when the temperature becomes higher, so as to prevent the corrosion of the machine parts. Because the preservatives added to the antifreeze will gradually decrease or become invalid with the extension of use time. What's more, some simply don’t add preservatives, which will have a strong corrosive effect on the parts. Release the antifreeze in time according to the temperature, and after the release of the antifreeze, the cooling pipeline should be thoroughly cleaned.Change the water and clean the pipeline regularlyIt is not recommended to change the cooling water frequently, because the minerals of the cooling water have been precipitated after a period of use. Unless the water is already very dirty, it may block the pipeline and the radiator. Do not replace it easily, because even if the newly replaced cooling water passes through It has been softened, but it still contains certain minerals. These minerals will be deposited on the water jacket and other places to form scale. The more frequently the water is replaced, the more minerals are deposited, the thicker the scale will be. Therefore, it should be based on actual conditions. Change the cooling water regularly. The cooling pipeline should be cleaned during replacement. The cleaning fluid can be prepared with caustic soda, kerosene and water. At the same time, maintain the drain switches, especially before the winter, replace the damaged switches in time. Bolts, sticks, rags, etc. cannot be used as substitutes.
Grid-connection plan and basic configuration of biogas generator sets (take two sets of 400KW biogas generator sets as an example) I. Introduction to the protection of biogas generator sets (1) The 400KW biogas generator set has a complete safety control system. It meets the requirements of JB/T9583.1-1999, NYT1223-2006 biogas generator set, and has the following safety protection devices: 1. Low engine oil pressure alarm, stop 2, engine overspeed alarm, stop 3, the engine cold water temperature is high alarm 4. High methane concentration alarm in the engine room 5. High engine cooling water temperature alarm 6, high engine oil temperature alarm 7, Ignition system fire alarm 8. Generator reverse power protection 9, generator undervoltage protection 10, generator overcurrent protection 11. All rotating parts are protected by steel mesh cover as a protective device. (2) Brief introduction of control screen function: 1. The control panel of the biogas generator set is a floor cabinet structure. The intelligent automatic air circuit breaker (AH) is selected, which has automatic over-current protection and reverse power protection. When over-current or reverse power occurs, it can automatically disconnect the main switch and send out an audible and visual alarm signal. The control panel is equipped with controllers, various display instruments, adjustment buttons, unit protection indicators, emergency stop buttons, etc., which are used to control and monitor the working conditions of the generator set. The start of the generator set is manually operated at the side of the machine, and the shutdown can be controlled at the side of the set, or by the emergency stop button on the control panel. 2. The control system is equipped with imported automatic paralleling control module (optional for users), which can automatically monitor and synchronize to meet manual and automatic paralleling. When multiple units are running in parallel, it can realize automatic load distribution function to meet grid and parallel operation Working conditions. The speed of the unit is automatically adjusted by the electronic speed control system, and it can also be adjusted in a small amount through the speed fine-tuning knob on the control panel; the unit voltage is automatically adjusted, and the voltage is adjusted by the voltage setting potentiometer on the control panel. The control panel is equipped with a floating charging device to provide charging power for the battery. II. Description of the grid-connected protection of the Green Ring biogas generator set 1.Short-circuit protection: Use the electromagnetic release of the main circuit low-voltage circuit breaker for short-circuit protection, and the operating current is set to 8-10 times the rated current. 2.Overcurrent protection: Use the delay release of the low-voltage circuit breaker of the main circuit to set it at 1.25 times the rated current of the generator. 3.Under-voltage protection: Install a voltage-loss release on the low-voltage short-circuit device of the main circuit to open the main circuit breaker when the generator voltage is lower than 50%-60% of the rated voltage. 4.Reverse power protection: When reverse power of 5%-15% of rated power occurs during parallel operation, the reverse power protection device opens the main circuit breaker within 10s. 5. Generator thermal protection: When the stator temperature exceeds 145℃, an audible and visual warning signal will be issued, and the main circuit breaker will be opened when the temperature exceeds 155℃. III. Grid-connected biogas generator set (1) The grid connection of generators should meet three conditions: 1. The voltage of the generator to be paralleled is equal to the voltage of the system. 2. The weekly rate of the generator to be paralleled is equal to the weekly rate of the system. 3. The phase angle of the generator to be paralleled is consistent with the phase angle of the system. (two) grid-connected plan Primary system plan (specifically subject to the generator manufacturer's configuration and the primary system design requirements of the electrical industry department) Plan 1: Generator-generator control cabinet-grid-connected protection cabinet-metering and outgoing circuit breaker cabinet- Incorporate into the low-voltage 400V power grid; Option 2: Generator-Generator control cabinet-Metering and outlet circuit breaker cabinet-Step-up transformer (10KV/35KV)-Metering and PT cabinet-Grid-connected protection cabinet-High voltage Isolating switch-power grid; 2. Relay protection configuration plan (specifically subject to the configuration of the generator manufacturer and the relay protection design requirements of the electrical industry department) In addition to the manufacturer’s standard configuration at the outlet of each generator, a relay is installed On the side of the electrical protection cabinet, an independent overcurrent protection device, an overcurrent protection device in the low-voltage direction, and a low-frequency protection are installed; in order to ensure the safe operation of the generator and prevent the system from sending power back to the generator, it must be at the generator outlet Install a reverse power protection device at the place. (Preferably the grid-connected comprehensive protection device commonly used in power systems) (The grid-connected cabinet of the generator is an "ordinary" high-voltage switch cabinet with a built-in circuit breaker. Because it is connected to the generator system and the grid system, it is installed with complete grid-connected protection The device plays the role of generator grid-connected, and is called "grid-connected cabinet"; the special point of this cabinet is that the protection installed is different from other outgoing switch cabinets, and it is generally equipped with directional overcurrent protection and current time limit quick-break protection , Low-voltage and low-cycle oscillating unloading protection, etc.) Conclusion: Optimal option one. IV. Design of external power grid lines The cross-sectional area of the external power grid line is considered according to the maximum load of the plant area and the capacity of the generator assembly. The grid-connected location is the low-voltage side or the high-voltage inlet side of the plant substation. For example: the capacity of the project's generator set is 2X400KW, the maximum load in the biogas station is 120KW, and the transformer type of the station is 400KVA, then the line of the external power grid is based on 2X400KVA, and the selection can be calculated according to the design specification. V. generator configuration requirementsGenerator configuration: biogas engine, Stanford/Siemens generator, public chassis, control panel, radiator, ignition system, mixer, battery pack, control start signal cable, generator starter, battery charging unit, fan cooling system The control unit (including cables within 50 meters), one waste heat boiler, two circulating water pumps, a generator biogas buffer tank and an indoor piping system, generator spare parts and information; 2. Provide two generator control panels One contact cabinet, one dedicated isolation switch cabinet for grid-connected outlets; 3.one control box screen for each of the and 400GF units and one set of automatic grid-connected devices.
Gradually in winter, pay attention to keep warm. Generator sets are used as the main backup power source for breeding enterprises and chemical enterprises, providing a stable power supply for the production and life of enterprises. As the main power supply, we also need our careful care to survive the cold winter safely.So what should I pay attention to when using and maintaining generator sets in winter? The precautions for daily maintenance of the generator set and some special considerations in winter require our attention.1. Replace the fuel. Generally, the freezing point of the diesel used should be 3-5°C lower than the seasonal low temperature to ensure that the diesel solidification does not affect the use of the generator set at low temperatures. Change the fuel in time according to local temperature changes.2. If the temperature in the replacement engine oil room is lower than 0°C, the viscosity of the lubricating oil suitable for other seasons will increase, which is not conducive to the lubrication of parts in the engine and affects the normal start of the engine. At this time, low-viscosity lubricating oil needs to be replaced. Generally, CF-4-15W-40 type lubricating oil can be selected to meet the lubrication needs of diesel engines in winter.3. The role of water jacket heater In winter, if conditions permit, the generator set can be equipped with a water jacket heater, so that the machine can maintain a certain "body temperature" and can easily operate at any time.4. Start the generator set correctly: some operators can start the diesel generator set quickly, and often use the start method without water (start first, then add cooling water). This practice will cause serious damage to the crew. Start the generator set according to the correct starting method to prolong the service life of the generator set: first cover the heat preservation quilt on the water tank, open the drain valve, and continuously pour 60-70℃ clean soft water into the water tank. Touch the water flowing out of the drain valve with your hands. Feel it, then close the drain valve, and then start the generator set.5. Precautions for low-temperature loading The diesel generator set has just started. Due to the low body temperature and high oil viscosity, the oil is not easy to fill the friction surface of the parts. If the generator set is operated with load at this time, the parts lack lubricating oil, which will cause serious wear and tear of the machine. In addition, plunger springs, valve springs and injector springs are also prone to breakage due to "cold brittleness". After the diesel generator starts to catch fire in winter, it should be idle for a few minutes at low and medium speed, and when the cooling water temperature reaches 60℃, put it into load operation.6. Correctly discharge water after shutdown. The generator runs at idling speed before shutdown. After the cooling water temperature drops below 60℃, turn off the engine and release the water. If the cooling water is discharged prematurely, the engine body will shrink suddenly when the internal temperature is high when it is attacked by the cold air, causing cracks in the diesel engine. When draining water, the remaining water in the body should be completely drained to avoid freezing and swelling, which may cause body damage. No matter what season, antifreeze can be used, which not only plays a cooling role, but also protects the diesel engine.
When this question is asked, you will think about cost, security and functionality of automatic natural gas generator . A manufacturer is expected to ascertain the source of raw material, reduce the price for raw material and use innovative technologies, so as to enhance the performance-cost ratio. Today the majority of the manufacturers would examine their raw materials before processing. They might even encourage third parties to check the materials and issue test reports. Strong partnerships with raw material suppliers are of great importance to the automatic natural gas generator manufacturers. Because this means that their raw materials would be guaranteed by cost, quality and quantity. Without the efforts of every employee, Xinshengan as a gas generator price brand cannot be so successful. 's diesel generator set is various in types and styles to meet the different needs of customers. This product features the required softness. During the processing of the fabric, the chemical softener has been added to remove the roughness and friction between fibers. It is made in strict accordance with the environmental management system. The product has good shock absorption property, hence it is loved by many people who may be exposed to tendons and ligaments injuries. It can be designed to be of a variety of styles.Under the principle of customer first, we will seriously consider customer suggestion, handle customer complaints, and strive to give solutions within one day.